ProPEX EP Plugs permanently or temporarily terminate the end of Uponor PEX tubing.
Note: ProPEX Tool is required. ProPEX Rings sold separately.
ProPEX® Engineered Plastic (EP) Plugs terminate Uponor crosslinked polyethylene (PEX-a) tubing ends and are available for use in hot and cold domestic potable water systems, residential fire sprinkler systems and hydronic heating and cooling systems.
Technical Data: Material: UDEL® Polysulfone, 20% Glass-reinforced (½" - 1"); Acudel® modified polyphenylsulfone (1¼" - 2")
Maximum Temperature (no pressure): 320°F (160°C)
Maximum Working Temperature/Pressure: 210°F (99°C) at 150 psi (1,034 kPa)
Installation: Use the appropriate ProPEX Ring for PEX-a tubing. Refer to the Uponor AquaPEX® Professional Plumbing Installation Guide, AquaSAFE™ Residential Fire Sprinkler Installation Guide or Uponor Radiant Installation Handbook for additional information.
Standards: NSF 14; NSF 61; ASTM F877; ASTM F1960; ASTM E84; ASTM E119; ASTM E814; CAN/CSA B137.5
Codes: IBC; IRC; IPC; IMC; UPC; UMC; NPC of Canada; NSPC
Listings: cNSFus-pw; cQAIus P321; HUD MR 1269; ICC-ES-PMG-1006; ICC-ES-PMG-1012; U.P. Code; IAPMO 253
Related Applications: PEX-a Plumbing Systems
Hydronic Radiant Heating and Cooling Systems
Snow Melting Systems
Turf Conditioning Systems
Permafrost Prevention Systems
AquaSAFE Fire Safety Systems