ProPEX EP and LF Brass Elbows make tight, 90-degree connections for Uponor AquaPEX tubing in supply and return mains.
The ProPEX® Engineered Polymer (EP) Elbow makes 90-degree connections for Uponor crosslinked polyethylene (PEX-a) tubing for use in hot and cold domestic potable water systems, residential fire safety and hydronic radiant heating and cooling systems. Each end of the elbow is manufactured with an Uponor ProPEX fitting for connections to Uponor AquaPEX® or Wirsbo hePEX™ tubing.
UDEL® Polysulfone, 20% Glass-reinforced (½ to 1")
Acudel® Modified Polyphenylsulfone (1¼" to 1½")
Radel® R Polyphenylsulfone (2")
Maximum Temperature (no pressure): 320°F (160°C)
Maximum Working Temperature/Pressure: 210°F (99°C) at 150 psi (1,034 kPa)
Installation: Use the appropriate ProPEX Ring for PEX-a tubing. Refer to the Uponor AquaPEX® Professional Plumbing Installation Guide, AquaSAFE™ Residential Fire Sprinkler Installation Guide or Uponor Radiant Installation Handbook for additional information.
Standards: CAN/CSA B137.5; ASTM F877; ASTM F1960
Codes: IPC; UPC; NSPC; NPC of Canada
Listings: IAPMO 3558; ANSI/NSF 14- and 61-certified; HUD MR 1269; ICC ESR 1099; UL 1821; ULC/ORD-C199P
Related Applications: PEX-a Plumbing Systems
Hydronic Radiant Heating and Cooling Systems
Snow Melting Systems
Turf Conditioning Systems
Permafrost Prevention Systems
AquaSAFE Fire Safety Systems